The Mercator Ardene Quattro exhaust fan is usually hardwired by an electrician to a switch. The installer can wire it so the fan and light work separately, from separate switches, or together from a single switch. The Ardene Quattro have an extraction rate of 220 m3/hr.
It is recommended to achieve a minimum of 10 air changes per hour in a bathroom, toilet or laundry, to remove excess moisture. To work out the recommended capacity needed for your room, calculate the volume of air in the room ( length x width x height, all in meters) and multiply this by the number of air changes to get the required air volume of the fan. (This will be adequate in most normal situations. We recommend that those clients who install in a bathroom who have a lot of glass and prefer to have warmer showers should get a fan double or more the recommended capacity.)
Note: If you install an exhaust fan with ducting, there will be a loss in capacity resulting in fewer air changes per hour.
220m3/hr (61 L/s)
- 4 x 275W heat lamps
- 1 x 42W R63 energy saving globe
- Cut Out Template
- Draft stopper
- 1.5m of 100mm flexible aluminium duct
- wall controller with 4 gang switch included for separate heat, light and fan control
Mercator Ardene Quattro 4 Exhaust Fan Features
- Ultra quiet and powerful 30W high quality ball bearing motor
- Thermal cut out feature safety
- Noise Level: 45 dB
Depth = 200mm
Thermal cut out feature safety = 80degrees celsius
Hole Size: 290mm x 290mm
Mercator provides a 12 month replacement warranty (see manufacturer’s website for more details).
**Fan & components must be installed by Qualified Persons unless a lead and plug is fitted for a DIY installation**